Recall: Voyager Heating and Air Conditioning Systems Recall by Trane Company
A name plate bearing each unit's model and serial number is located on the outside sheet metal at the end of the unit where the propeller fan is visible on top, directly to the left of the exposed outdoor coils.
PROBLEM: One of the three internal flue gas tubes extending from the heat exchanger can separate from the heat exchanger. This could allow flue gases, including carbon monoxide, to enter the building airstream. This could result in serious injury or death to building occupants.
INCIDENTS/INJURIES: None reported.
WHAT TO DO: Call the local independent Trane or American Standard dealer for a free inspection and replacement, if needed. Trane will completely replace the heat exchanger end plate and internal flue gas tube assemblies in all recalled units at no cost to the consumer. For assistance in locating a local independent dealer, contact Trane at (800) 940-1344 between 7:30 a.m. and 4:30 p.m. CT Monday through Friday, or visit the firm's web site at www.trane.com.
|Justia Consumer Recalls Household & Office Heating, Ventilation & Air Conditioning Air Conditioners|